Meters and Controls for Water Booster Station. ATG Provided complete control package.
Chemical Feed Pump Controls for Water Booster Pump Station
Aqua Technology Group provided a replacement water booster station flow meter / differential pressure transmitter (DP Transmitter). The existing application used a BIF Universal Venturi Tube to provide flow indication to an older Foxboro d/p Cell / Flow Transmitter that had failed. ATG replaced the old Foxboro transmitter with a new Rosemount differential pressure transmitter and hardware designed to directly bolt up to the existing venturi tube piping. This flowmeter setup allowed for a rapid deployment by our field engineer and the booster station flow meter being placed immediately into service. The output of the D/P Cell feeds into a local RTU where the flow meter’s 4-20 mA signal is scaled and totalized before being sent to the rest of the SCADA system for control and analysis.
Get your Water Booster Station Flow Meter Project Started Today!
Water Quality Instruments and Monitoring for Water Garden, Aquarium and Nature Preserve.